The electrical sub has finished their work and the local inspector did his walk-through. We got the sticker on our box saying we are ready for service, but the real shocker came later that day.
Phil, the local L&I inspector, called our sub to give the three install techs a big “atta boy!” He continued on to say their quality of work and care of design was above par and he was very impressed with all the work they put into the house.
I am too.
Multi-Wire Branch Circuits
Electrical work is a special interest area of mine and I was very keen to see first hand how the pros do it. Frankly, I was surprised to see them use almost every breaker in this 200A panel, but their distribution system is very granular and makes a lot of sense.
The installers used an interesting trick to save on time and copper as well: Instead of pulling two runs of 12/2 cable (black, white, bare) across the house for systems like the dishwasher and disposal, they pulled a single run of 12/3 cable (black, red, white, bare). This design is simple, elegant, and cost-effective. The red and black wires distribute opposite phases of electricity to a breakout box elsewhere in the house. At that point, the 12/3 is connected to two 12/2 lines and sent on to the final destination.
That means you have two 120V branches using the same common (white) and ground (bare) lines back to the box. The beauty in this design is that the red and black wires are opposite phase, so their return current cancels out on its way back to the box. Imagine your dishwasher is running and drawing 10 Amps on black and your disposal draws another 8 Amps on red. The white common wire would only carry 2 Amps back to the box. If the MWBC was wired correctly putting the two appliances on opposite phases, the return current is the difference between the hots.
As with all things electrical, this technique must be used with caution. Improperly wiring both hots to the same phase creates an additive current on the common wire and disconnecting the common with a load connected can cause a dangerous over/under voltage situation. Consult a professional before mucking around with your wires!
Once important thing about most MWBC is their ability to trip independently despite being tied together like a normal dual-phase breaker. Unless you have split phase at a single outlet or are using both phases in one appliance, the breakers need not trip simultaneously when overloaded. However, they must be connected with a tie which forces you to turn both breakers off simultaneously while servicing either circuit. This is important because if you just turned off the disposal breaker and someone started the dishwasher, the return current from that appliance would energize the shared common line at the disposal. Check out these links for more information on multi-wire branch circuits and independent trip MWBC.
The garage floor just went in yesterday. I’m almost a bit sad to see it in because now I can’t park my car in the garage until the driveway is poured in several weeks. My Prius just doesn’t have the guts to make the eight inch leap from the dirt outside.
This means that the garage doors will soon be appearing and I can get a head start on building my airplane in there*.
Siding Going Up
Massive scaffolding appeared on-site late last week. On Monday, the siding subs arrived early to start work wrapping the house and nailing up the siding boards.
A house in this stage has an unnerving look. Once the siding is up, the house will be in the “uncanny valley” where it looks off but you just don’t know why at first–like a poorly done computer animation or a person with shaved eyebrows. It is the window and roof trim that goes unnoticed until it isn’t there. Its absence is conspicuous and jarring, making a freshly sided house seem strange.
Once the siding pros have completed installing the broad boards, they’ll go back and trim the windows and add the cedar accent shingles. The painters will be by some point later on to finish the job. Without inquiring, I presume it will be about the same time they return to paint the inside of the house.
* Just kidding… I’ll wait until the drywall is up.